* The preview only show first 10 pages of manuals. Please download to view the full documents.
HEATING TECHNIQUE Centrometal d.o.o. - Glavna 12, 40306 Macinec, Croatia, tel: +385 40 372 600, fax: +385 40 372 611
TECHNICAL INSTRUCTIONS for regulation, use and maintenance of pellet stove
CentroPelet ZV14 TUZS-4-2014-ENG
GB Dear Customer, Congratulations on your purchasing an pellet boiler stove! We would like to remind you that pellet boiler stoves are the most innovative heating solution generated by the most advanced technology, characterised by high-quality manufacturing as well as a simple and elegant design. Ideal for any type of room, these products contribute to comfort thanks to the cosy heat that only flames can radiate. This manual will help you use your pellet boiler stove properly. Therefore, read it carefully and thoroughly before using the unit. Stoves are fuelled only by wood pellets, up to 6mm in diameter. They are fitted with an exchanger that allows reaching a heat yield of approx. 90%. Pellet boiler stoves are fitted with a timer-thermostat that ensures an autonomous management of the stove as it can be programmed to turn on and off up to 4 times per week. Pellet boiler stoves take the heat to the radiators in the heating system, with a thermal power that is adjusted according to the space to be heated: just set the heating system water temperature manually. Recommended temperature: between 60° and 75°. Pellet boiler stove also heats the room where it is installed through a natural convection air- system. Pellet boiler stoves have been equipped with highly advanced automatic devices and control and safety systems that ensure efficient and practical operation. Installation and maintenance operations should be carried out by qualified personnel, in compliance with the laws in force and according to the indications specified by the Manufacturer. This use and maintenance manual is an integral part of the product. Before using, installing or servicing the product, read the indications contained in this manual carefully. This pellet boiler stove should only be used for the intended use it has been designed for. Therefore, the user shall be responsible for any damage to people, animals or things resulting from misuse of the product.
CAUTION! The first two or three times your pellet boiler stove is started, fumes emitted by the varnish may cause unpleasant smells due to hardening. Therefore, it is advisable to air the room properly, and avoid staying long in front of the pellet boiler stove.
Installation should be carried out by qualified personnel, who will be fully responsible for installing the product and ensuring its proper operation. The Manufacturer shall not be responsible in case of installation by unqualified personnel or without complying with the general warnings and installation instructions. After unpacking the unit, check all the parts are in good conditions and that no item is missing. Otherwise, contact the dealer from which you purchased your pellet boiler stove. Before installing the unit, it is advisable to clean all the ducts and pipes in the system very carefully in order to remove any scales that may affect the stove correct operation. Whenever the pellet boiler stove is not used for a long time, it is advisable to carry out the following operations: The pellet boiler stove extraordinary maintenance should be carried out at least once a year. This operation should be For safety reasons, it is advisable to remember that:
In the event of a fire, disconnect the power supply, use an extinguisher and call the fire fighters if necessary. After that contact the Authorised Assistance Centre.
Aproximative dimensions (mm).
Weight Flue pipe diameter Air intake pipe diameter Power Supply Min. electrical input Max. electrical input Hopper capacity
approx. Kg 130 80 mm 50 mm 3/4” 220V - 50Hz 90 W 350 W only start phase 17 kg
Pellet Boiler stove start up Preliminary checks
CAUTION! The brazier should be cleaned before each starting.
Before switching on the pellet stove, make sure that the pellet hopper is full, the combustion chamber is clean, the glass door is closed, the power supply plug is connected and the switch on the back is set to “1.”
Control Panel (Pict. 2) della termostufa e per uscire dalla programmazione. Buttons and are used to adjust temperature, for displays and for the programming functions. Buttons
are used to adjust heating power.
Button is used to adjust temperature and programming functions. The upper and lower displays are used to view different messages. Pict. 2 2
How to load pellets in the tank You can load pellets in the tank through the door on the upper part of the stove. Join the following procedure to load pellets: Starting the Stove Press button for a couple of seconds until the pellet boiler stove starts. (?L will be displayed on the upper display and #%%on the lower one. During this phase the unit will carry out a diagnosis (around 20 seconds) on the fume extraction system.
4 6 5
The LED is on when the parameter UT01 on the menu is not on OFF and the weekly or daily programming are set.
The LED starts up every time the stove is loading pellets The LED blinks when the board signalises a change in temperature or power set by the infrared remote control.
The LED is on when the room temperature reaches the value set on the menu SET Water.
The LED blinks to indicate that you are that you are modifying the temperature set.
The LED switches on when the water circulator is working.
CAUTION! It is advisable to use dry wood pellets, up to 6 mm in diameter.
.1#& 911& is the next phase, which indicates pellets should be fed. The glow plug will heat up to light the fire.
When the fume temperature is 50º C (approx. 10 minutes), the pellet boiler stove will confirm the ignition: (GP' will be shown on the upper display and 10on the lower one. After this phase, which lasts around 5 minutes, the heating power (e.g. NM ) and the room temperature (e.g. x), will be simultaneously shown on the upper display, and the system delivery water temperature will be shown on the lower display.
If the flame does not start up correctly within 10 minutes, the pellet boiler stove jams: you will read the words #.#4 on the upper display and the words 01#%% blinking on the lower display. Wait 10 minutes until the cooling phase is completed, open the door, empty the brazier and start a new light-up.
REMARKS: In case of repeated ignition lock-outs, while pellets are fed regularly, there may be a problem caused by a failing electric glow plug. In this case, while you wait for a technician, the pellet boiler stove can be manually started by using solid fuel cubes (firelighters). Manual starting procedure:
Working power and water temperature settings
The heating power is set by the and . A heating pokeys wer at Po 9 is suggested during the first working hours of the stove. To set the water temperature press the key only once. You will see the words 5CR*M blinking on the upper display. You will read the water temperature on the lower display. Use the keys and to increase and reduce the wished value. Water temperature range: 30°C – 80 °C
To set the room temperature, press the key twice: you will see the words 5'6#4+# blinking on the lower display. You will read the set temperature on the upper display. Use the keys and to change the value.
Room temperature range: 7°C – 40 °C
Turn off the pellet boiler stove by pressing button , for a couple of seconds until 1((is shown on the upper display.
CAUTION! Do not use any flammable liquid to start the stove. During the reload phase, do not bring the bag of pellets in contact with the hot pellet boiler stove.
Room temperature setting
Procedure to turn off the pellet boiler stove
Pellet feeding will stop immediately but the pellet boiler stove will continue working until the accumulated heat is fully consumed, turning itself off automatically after approx. 30 minutes.
REMARKS: The pellet boiler stove is fitted with an automatic device that allows cleaning the brazier after a given period of time: when this time is detected, the stove fire automatically reduces and 27.(+4'is shown on the display. After some minutes, the pellet boiler stove will start working regularly.
WARNING Do not unplug the power plug to turn off the pellet boiler stove; wait until the automatic shutdown cycle finishes: the continuous operation of the fumes extraction fan is normal and may indicate that the stove is still hot. In the event of low temperatures, it might happen that the stove - although switched off - starts the smokes fan and circulator for some minutes in order to prevent ice formation on the pipes of the system. in the event there is a power drop, the main board will exhaust the smokes residuals as soon as the power supply is back on. In order to do that, the main board will increase the speed and show the words “Cool FIRE” on the display. As soon as the cooling phase has been completed, the stove will automatically start up working as it was set before the power drop.
Heating timer-thermostat The heating timer-thermostat function is used to program the pellet boiler stove to automatically turn on and off within a period of one week. To access programming, hold down button for around three seconds, “UT01” will be shown on the upper display: by pressing button several times and referring to the table below, the stove can be programmed according to your needs. Press button to exit the programming phase at any time. These are the heating timer-thermostat parameters:
H. timer-thermostat enabling and disabling. Day of the week setting
Current hour setting
The meaning of the user parameters are explained in detail below: UT01 Heating timer-thermostat enabling and disabling and current hour setting. This parameter is used to set the current day of the week or to deactivate the set programming. Press buttons and to select the desired value as shown in the following table:
Heating timer-thermostat disabled
From 00 to 23
Current minutes setting
Technical parameters setting Reserved
Pellet boiler stove first start- From 00:00 to 23:50 with 10-minute steps up time adjustment
Pellet boiler stove first shut- From 00:00 to 23:50 with 10-minute steps down time adjustment
Week day selection, first from 1 to 7 time activation
Pellet boiler stove second From 00:00 to 23:50 with 10-minute steps start-up time adjustment
Pellet boiler stove second From 00:00 to 23:50 with shutdown time adjustment 10-minute steps
Week day selection, second from 1 to 7 time activation
Pellet boiler stove third From 00:00 to 23:50 with 10-minute step start-up time adjustment
Pellet boiler stove third shu- From 00:00 to 23:50 with 10-minute step tdown time adjustment
Week day selection, third from 1 to 7 time activation
Pellet boiler stove fourth From 00:00 to 23:50 with 10-minute steps start-up time adjustment
Pellet boiler stove fourth From 00:00 to 23:50 with shutdown time adjustment 10-minute steps
Week day selelction, fourth from 1 to 7 time activation
From 00 to 60
Example: start the pellet boiler stove manually (without programming) so that the heating timer-thermostat is disabled.
to go to the following parameter.
UT02 Current hour setting This parameter is used to set the current hour, press buttons and to select the current hour. Press button to go to the following parameter. UT03 Current minutes setting Press buttons and to adjust current minutes. Press buttons to go to the following parameter. UT04 Technical parameters setting Press button to go to the following parameter.
UT05 Pellet boiler stove first start-up time adjustment This parameter indicates the time at which the pellet boiler stove will be started: use buttons and to set the desired time, with 10-minute steps. Press button to go to the following parameter. UT06 Pellet boiler stove shutdown time adjustment This parameter indicates the time at which the pellet boiler stove will be turned off: use buttons and to set the desired time, with 10-minute steps. Press button to go to the following parameter. UT07 Week day selection Press button to select the days of the week. Press button to enable (ON) or disable (OFF) the pellet boiler stove start-up day as shown in the following table:
ON1/OFF1-Yes or No
ON2/OFF2-Yes or No
ON3/OFF3-Yes or No
ON4/OFF4-Yes or No
ON5/OFF5-Yes or No
ON6/OFF6-Yes or No
ON7/OFF7-Yes or No
In the following example, the pellet boiler stove is only started on Saturdays and Sundays. Day 2 Day 1 Day 2 Day 3 Monday Tuesday Wednes. Thurs. off 1
Confirm and continue with key UT08
Day 2 Day 2 Day 2 Friday Saturday Sunday off 5
continue as indicated above to set the second, third and fourth ignition times.
If the stove is controlled by an external thermostat, when the thermostat reaches the preset temperature, '%16'4/ will be shown on the pellet boiler stove display.
CAUTION! the room temperature thermostat does not turn off and on the pellet boiler stove; it sets the stove in saving mode.
Remote Control The remote control (Pict. 3) s used to adjust water tempe To start the pellet boiler stove, press keys and simultaneously. The pellet boiler stove will automatically enter the starting phase. Press keys and to adjust water temperature, and use keys and to adjust operating power. To turn off the pellet boiler stove, hold down keys and simultaneously. “OFF” will be shown on the Pellet boiler stove display.
In the event of a working defect, the system informs the user about the type of failure occurred. The following table summarises the alarms, kind of problem and possible solution:
Upper Lower display display
Kind of failure
- the pellet boiler stove Fill in the tank with pellets cannot start up Start up again - this is the first light-up
- the pellet boiler stove Fill in the tank with pellets switched off while working
SOND broken or not connected qualified FUMI to the pcb stance
The water temperature exceeds 90°C. The circulating pump is blocked or there is no water in the hydraulic system
The smokes sensor is Contact an authorised and technical assi-
Pict. 3 HOT H20
Check the power supply on the pump. Check limestone does not block the pump impeller
The water sensor is not Check the water sensor is
connected SOND connected H20 There is a short circuit on Contact an authorised quathe water sensor
lified technical assistance
sensor failure HOT The smokes temperature Smokes Contact an authorised quaTEMP exceeds 280°C lified technical assistance
As soon as the power supply is back, the stove starts There is no power sup- a cooling cycle. After comply pleting the cycle it starts working automatically
Contact an authorised Smokes extractor blo- qualified technical assicked or broken stance
To replace the 12 volt battery located on the back of the Replace the battery observing the correct polarity (Pict. 4).
SSize: IZE: 12V 12V
Clean the flue or check there are no obstructed grids near the smokes exhaust Re-set the safety thermostat Pellets tank overheating for pellets on the back of the stove. If the problem occurs again, contact an authorised qualified technical assistance Too high water tempera- Re-set the safety thermostat for water on the back of the ture stove. If the problem occurs again, contact an authorised qualified technical assistance The system pressure
ALAR PRESS does not reach 0,5 bar or exceeds 2,3 bar
The stove has worked for 1300 hours. Supplementary maintenance required
Reduce the system pressure Charge the system Contact an authorised qualified technical assistance
Regular checks should be carried out by the user, who should only contact the Technical Assistance Service if no solution is found.
Failure on electrical devices Failed light-up If the flame does not light up during the switching on or if the smokes temperature does not reach a suitable value in the foreseen time gap, the stove switches off and you will read the words #J?P0M#AA on the display. cooling phase is completed, clean the brazier and start a new light-up. Switching off while working The stove suddenly switches off while working (for example because it has run out of pellets in the tank or because the motor reducer for pellets loading got broken). The stove continues working until the pellets left in the brazier ends. You will then read the words #J?P0M(GPC on the display and alarm. Wait until the cooling phase is completed. Clean the brazier and start a new light-up.
These alarms remind you that the brazier must be cleaned and installed correctly before switching on the stove.
Smokes exhaust safety A mechanical depressor checks the correct depression for a proper smokes exhaust. On the contrary, if the flue is obstructed, the pellet boiler stove switches off and you will read the words #J?P&CN(?GJ on the display. Pellets temperature safety In the rare event there is a too high temperature in the tank, the thermostat for pellets safety with manual reset creates an alarm #J?P5GA(?GJ stopping the pellet boiler stove. You need to reset the system working on the device placed on the back of the stove (Pict. 5)
Water temperature safety In the event the water temperature exceeds a limit value of 100°C, the thermostat for water safety lets the stove switch off. You will read the words #J?P5GA(?GJon the display. Once you have waited a minimal time required for water cooling, you need to reset the thermostat placed on the back of the stove (fig. 5). Manual reset thermostat
There is no power supply In the event of a power drop longer than one minute, the pellet boiler stove can exhaust some smoke in the room: this causes no risks. As soon as you have the power supply again, the pellet boiler stove will have the words %MMJ(GPC on the display. After completing the cooling phase, the stove will start up again automatically according to the previous settings.
Pict. 5 water
CAUTION! do not attempt to start the pellet boiler stove before the required time or it may get blocked. If this occurs, switch off the switch on the back of the pellet boiler stove for 1 minute, set it on again and wait 10 minutes before starting the stove again.
Electrical safety In the event of an electrical shock (lightning), the pellet boiler stove is protected by a fuse 2,5 A 250V which is placed on the back of the stove near the cable for power supply. Extract its box and replace the fuse.
CAUTION! the power socket where the pellet boiler stove is connected should be fitted with “earth connection complying with regulations in force.” The Manufacturer shall not be held responsible for damage to things or people resulting from negligent installation.
System pressure safety The system pressure is checked electronically and needs to be between 0,5 and 2,3 bar. If this is not the case, the pellet boiler stove signalises an alarm and shows the words “Alar Press” on the display. Check the system pressure keeping the key pressed for some seconds. You will read the bar value on the display. The safety valve keeps anyway the value under 2,5 bar letting the exceeding water flow out automatically.
Cleaning of the pellet boiler stove The pellet boiler stove requires an easy and detailed cleaning in order to grant always efficient performances and working. While you are cleaning the inner parts of the stove, you can start up the smokes exhauster to avoid ash to discharge. To activate this function, press the key and then the key you will read the words “PUL STUF” (cleaning of the stove) on the display. In order to stop the fan, you just need to press the key for a longer time waiting that a cleaning phase is completed (255 seconds).
Every three or four burnt pellet’s bag: open the lower door and unscrew the two knobs holding the inspection Pict. 8
EVERY DAY: remove and clean the brazier (Pict.6) Pict. 6
remove the inspection drawer (Pict. 9), empty it and clean only the wall and corners using a vacuum cleaner or specific tools. Pict. 9
Refit the inspection drawer and tighten up the two knobs carefully, taking into account tightness. Close back the lower door.
FROM TIME TO TIME: clean the exchanger every two days. When the stove is cold, use the scraper on the front grid to clean the pipes.
Cleaning the glass: clean the pyroceram of the central door totally clean. Suitable detergents can also be used.
CAUTION! Do not clean the glass while the pellet boiler stove is working. Pict. 7 scraper
Cleaning the flue: the flue should be cleaned at least twice a year or whenever required. If there are horizontal sections, it is necessary to check and remove any ash or soot deposits before they obstruct the passage of fumes.
CAUTION: if the pellet boiler stove is improperly cleaned or not cleaned at all, the following operation problems may occur: sulting in poor output.
Centrometal d.o.o. shall not be responsible for possible incorrect data caused by printing errors or error made in transcription and all ﬁgures and diagrams are for explanatory purposes only and relevant adjustment have to be made at the spot. In any case, it reserves the right to modify its products as deemed to be required and useful without any prior notiﬁcation.
Centrometal d.o.o. Glavna 12, 40306 Macinec, Croatia central tel: 040 372 600, fax: 040 372 611 service tel: 040 372 622, fax: 040 372 621
www.centrometal.hr e-mail: [email protected]